Dust explosion preventions and mitigations
Solutions to prevent and mitigate powder explosion in ATEX environment
Do you have a question, a remark ? Please contact the author at email@example.com
Solids Handling Safety
# Dust explosion physical properties # MIT - Minimum Ignition Temperature of dust
A dust explosion risk analysis (often called ATEX risk assessment) aims at identifying the ATEX zones, where an explosion can occur, defines the risk associated with any potential source of ignition, and propose measure to avoid or mitigate the risk.
This page is detailing the solutions to avoid an explosion, or to mitigate it if it happens.
2. Explosion prevention
Avoiding the source of ignition
When an ATEX area has been identified, which means that any point of time, a dust cloud can be present in explosive concentration, the 1st attempt of the process designer or operator should be to avoid the risk of explosion. Most of the time the approach is based on making sure that there will be no ignition source in the area.
The sources of ignition, and possible measures to avoid them is detailed in the following table :
Table 1 : sources of ignitions and how to avoid them
Use of an inert gas
When the measures listed above cannot be ensured, it is still possible to avoid the ignition by inerting the process. The oxygen concentration is then not enough to allow a combustion. The process can be gassed with nitrogen or carbon dioxide for this purpose. This can be quite costly and requires some specific process measures and safety chains to make sure the process is actually inerted.
It also works only inside the process equipment, it is not
valid in the immediate surrounding of the process which may
also be an ATEX zone.
Making sure there is no deposit of dust outside the process is also a measure, for certain zones and situation, to make sure dust will not be put in suspension and create an hazardous atmosphere.
3. Explosion mitigation
In certain cases, the explosion risks cannot be controlled by simply removing the source of ignition, or inerting is too complex and costly. In this case, the ATEX risk assessment should show that the risk has to be mitigated.
Of course, all good practices MUST STILL BE IMPLEMENTED TO PREVENT THE EXPLOSION, even if mitigation measures are in place.
Confinement - explosion resistance
The 1st possibility to mitigate the effect of an explosion is to have a system able to resist to the present increase in case of explosion and isolate the explosion inside a process area. It can typically be used for powder having a Pmax < 10 bar g and is often used in milling equipment.
The equipment must be calculated and certified for Pmax and
physical barriers like valves, must be used to isolate the
explosion. This solution is efficient but the equipment may
be damaged during the explosion and have to be replaced.
The 2nd solution is to allow a part of the installation to open at the very beginning of the explosion, and vent the explosion outside of the process equipment. Such venting is usually done thanks to a bursting disc or an explosion panel positioned on a hopper or silo.
The size and opening pressure of the venting equipment is very important to ensure a good protection in case of explosion and should be calculated by a reputable company, from the explosion characteristics of the dust. As for other explosion protection systems, it is necessary to isolate the explosion if it happens and keep it in the area of the vent. The explosion should not be allowed to propagate to several process sections.
There is a potential hazard where the explosion is vented, due to the pressure wave and to flames. It is necessary to vent the explosion in a safe area, without the presence of people. In some cases, it is possible to install a flame arrester if the venting is to be done inside a building.
The last strategy that can be put in place to mitigate an explosion is to suppress it. The suppression can be done thanks to chemicals injected in the process and that will stop the explosion prior it reaches hazardous pressures.
The installation of such system requires specific knowledge and a reputable company must be contracted to carry the design and the installation.
Such system should be coupled with an isolation system as well.
As mentionned above, it is necessary to isolate the explosion happening in one area of the process, to the other area, to avoid that an explosion on one side triggers another explosion somewhere else.
Active isolation systems : Quick acting valves
Passive isolation systems : Ventex valves, airlock rotary valves
The measures put in place to
avoid ignition sources and the type of explosion
mitigation chosen, must
be described in the ATEX risk analysis and the
measures to put in place explained. Conclusions of the
risks analysis must be implemented by the factory.
|Do you want to
know more ?
www.powderprocess.net is covering all aspects of solids and powder processing and handling
The pages below will probably interest you !
Answers ALL your questions on pneumatic transport
of MIX / MEASURING DEGREE OF MIXING
All you need to know about measuring the degree of mixing (Coefficient of Variation) of a dry mix
OF POWDERS / DEMIXING
All on the physical phenomena causing segregation of particles and how to avoid them
All on main size reduction processes, key equipement, design consideration..etc..
All on powder key physical characteristics, among others : flowability, density...etc..
All equipment found in bulk solids handling industries, explained, with design tips...
|You can find much more through the menus at the top of the page !|