Electrical Equipment in zone ATEX (dust)
Risks associated with electrical equipment in dust ATEX areas
Do you have a question, a remark ? Please contact the author at firstname.lastname@example.org
Solids Handling Safety
# Dust explosion physical properties # MIT - Minimum Ignition Temperature of dust
Electrical equipment are necessary for the process, it includes motors, instrumentation, load cells, control cabinet...etc... It happens that such equipment have often to be positioned within an ATEX zone. In order to be safe, such electrical equipment must have a specific design.
In case of damage, electrical
equipment can generate sparks at electrical connections
which, if they enter in contact with a dust cloud, can
ignite the powder and create an explosion. Some
equipment, like motors, can also generate heat that could
be high enough to make the dust burn.
2. Equipment design and certification
In order to be used in a zone susceptible to have a dust cloud, the electrical equipment must be dust tight. According to the resistance to dust ingress, it will be certified either for zone 20, 21 or 22.
Typically IP5x (zone 22 for non conductive dusts) and IP6x (zone 20 and 21, and zone 22 for conductive dust) equipment will be used in those areas. Those standards should guarantee no dust infiltration in enclosure or at cable glands. Knowing the IP rating is necessary but not sufficient for qualification in ATEX zones, the equipment installed or modified after 2003 MUST be marked with the Ex sign and must comply with the ATEX zone in which they will be used.
The suppliers must also indicate the maximum surface temperature of the equipment. In any case, this maximum temperature must be lower than the MIT and SIT of the powder that can come in contact with the electrical equipment.
Many parameters have to be taken into considerations to certify an equipment, but basically the logic behind the protection against dust explosion is to avoid the ingress of the dust in the equipment, and make sure it will not overheat to hazardous levels.
The maintenance must also be perfect to keep the equipment compliant over time.
Note that there are also other types of ATEX protections that can be used : pressurization, intrinsic safety or molded compounds. These are more specialized applications.
The zoning definition and the
rating and maximum temperature of the electrical
equipment to be used in those areas, must
be described in the ATEX risk analysis and the
measures to put in place explained. Conclusions of the
risks analysis must be implemented by the factory.
|Do you want to
know more ?
www.powderprocess.net is covering all aspects of solids and powder processing and handling
The pages below will probably interest you !
Answers ALL your questions on pneumatic transport
of MIX / MEASURING DEGREE OF MIXING
All you need to know about measuring the degree of mixing (Coefficient of Variation) of a dry mix
OF POWDERS / DEMIXING
All on the physical phenomena causing segregation of particles and how to avoid them
All on main size reduction processes, key equipement, design consideration..etc..
All on powder key physical characteristics, among others : flowability, density...etc..
All equipment found in bulk solids handling industries, explained, with design tips...
|You can find much more through the menus at the top of the page !|